DSL Conductor bar – track are super finished and cross section is maintained to achieve required ampere. The material for track is G.I. (Galvanized & Copper) Conductors shall be accurately aligned to ensure positive electrical contact between the collector and the conductor. Separate conductors shall be provided for each phase. Insulation cover shall be rigid PVC. Range of Ampere available with the material of G.I. & Copper.
G.I. : 60 Amp. to 125 Amp.
Copper : 120 to 250 Amp.
|Type||PIN Jointed Type Busbar System|
|Conductor Material||Galvanized Or Copper|
|Insulation Type||PVC (IP35)|
|Ampere Capacity||G.I. : 60 to 125 Amp. |
COPPER : 120 to 250 Amp.
|Pole Type||1 Pole : Individual.
4 Pole. : RYBG |
|Jointer Type||Pin Jointed.|
|Standard Length||4.0 Mtr. (4000mm)|
|Mounting Bracket Distance Pitch||1000mm.|
|Busbar Distance Pitch||42mm. (Center)|
|Hanger Clamp||4 Pole : Per Mtr. 1 No. |
1 Pole : Per Mtr. 4 Nos.
|Anchor Clamp||Per 50 Mtr. 4 Nos.|
|Splice Cover||Splice cover is used to cover each joint.|
|End Cap||End Cap is used to cover DSL ends on either side. That is required one for one Bar/phase.|
|End Power Feed||For DSL system that is powered from ends,|
"End power feed" is required for Power supply of Bus bar system. That is required separately for each phase.